Rapid Shutdown Solutions
Yaskawa Solectria Solar provides PV inverter product solutions to meet NEC 2014 Rapid Shutdown requirements.
CODE REQUIREMENTS - NEC 2014 RAPID SHUTDOWN (Article 690.12)
PV system circuits installed in or on buildings shall include a rapid shutdown function that controls specific conductors in accordance with NEC 2014, Article 690.12 (1) through (5). These requirements include:
1. Rooftop PV installations
2. Rapid shutdown equipment placement:
a. 10 feet from array (equipment outside building) or
b. 5 feet from array (equipment inside building)
3. Shutdown to 30V & 240VA in 10 seconds
4. Correct stickers/signage
5. All PV equipment listed and identified
SOLUTION: Yaskawa Solectria Solar Residential PVI 3800-7600TL inverters and Rapid Shutdown Combiner Box
REQUIREMENTS: Installer must wire 5VDC control signal to inverter from Rapid Shutdown Combiner Box.